1 Published under s. , Wis. Stats., by the Legislative Reference Bureau. 15 SAFETY AND PROFESSIONAL SERVICES SPS Chapter sps 362 . BUILDINGS AND STRUCTURES. SPS Administration. SPS Secondary Roof drainage. SPS Definitions. SPS Roof covering classification. SPS Cheese factories classified as F 2 occupancy. SPS Roof covering materials. SPS Pyrophoric materials. SPS Roof slope. SPS Classification of institutions with 5 or fewer persons receiving SPS Roof snow load. medical care. SPS Alternate standards. SPS Use and occupancy classification. SPS Live loads. SPS Special detailed requirements based on use and occupancy. SPS Snow loads. SPS Chapter ATCP 93 compliance. SPS Roof drains. SPS Aircraft storage.
2 SPS Earthquake loads. SPS Hazardous materials. SPS Structural tests and special inspections. SPS Storm shelters. SPS Definitions. SPS Building height and number of stories. SPS Deep foundations. SPS Allowable building area. SPS Ground improvement. SPS Incinerator rooms. SPS Basement floor base course. SPS Allowable materials. SPS Presumptive load bearing values for saturated soils. SPS Definitions. SPS Shallow post foundations. SPS Exterior Walls. SPS Foundations. SPS Fire wall identification. SPS Frost protected shallow foundations. SPS Chute discharge room. SPS Deep foundations. SPS Ducts and air transfer openings. SPS Shotcrete clearance. SPS Calculated fire resistance. SPS Empirical design of masonry.
3 SPS Fire protection systems. SPS Welded Connections. SPS Definitions. SPS Steel trusses spanning 60 feet or greater. SPS Automatic fire sprinkler systems. SPS Wood trusses spanning 60 feet or greater. SPS Alternative automatic fire extinguishing systems. SPS Girder ends. SPS Fire alarm and detection systems. SPS Glass and glazing for elevators. SPS Smoke control systems. SPS Gypsum board and plaster. SPS Carbon monoxide detection. SPS Water resistive barriers. SPS Egress for outdoor areas. SPS Electrical code. SPS Exits. SPS Additional criteria for toilets. SPS Accessible means of egress. SPS Plumbing code. SPS Doors, gates, and turnstiles. SPS Plumbing fixtures. SPS Stairway width.
4 SPS Drinking facilities. SPS Floor level exit signs. SPS Elevators. SPS Guards. SPS Hoistway enclosures. SPS Corridor continuity. SPS Standardized fire service elevator keys. SPS Spaces under bleachers and grandstands. SPS Machine rooms. SPS Design of Type A and B units. SPS Special construction. SPS Scoping requirements limited access spaces. SPS Blower equipment. SPS Accessible route. SPS Temporary structures. SPS Dwelling units and sleeping units. SPS Pedestrian walkways and tunnels. SPS Signage. SPS Swimming pool enclosures. SPS Natural ventilation. SPS Encroachments into the public right of way. SPS Interior environment. SPS Safeguards during construction. SPS Court drainage. SPS Protection of adjoining property.
5 SPS Toilet rooms. SPS Referenced standards. SPS Exterior walls. SPS Appendices. Note: Chapter Comm 62 as it existed on June 30, 2002 was repealed and a new SPS Definitions. (1) ADDITIONS. These are Chapter Comm 62 was created, Register December 2001 No. 552, effective July 1, 2002. Chapter Comm 62 was renumbered Chapter sps 362 under s. (4) (b) 1., department definitions for this Chapter in addition to the defini- Stats., Register December 2011 No. 672. tions in IBC section 202: Note: Chapters SPS 361 to 366 are affected by 2017 Wisconsin Acts 59, 198, (a) High piled combustible storage means storage of com- 243, 317, 329, 330, and 331. Future rule making will update chs. SPS 361 to 366.
6 To reflect this legislation. bustible materials in closely packed piles or on pallets, racks, or shelves where the top of storage is greater than 12 feet in height. SPS Administration. The requirements in When required by the fire code official, high piled combustible IBC Chapter 1 are not included as part of chs. SPS 361 to 366. storage also includes certain high hazard commodities, such as Note: The sections in this Chapter are generally numbered to correspond with the rubber tires, Group A plastics, flammable liquids, idle pallets, and section numbering in the IBC, , s. SPS corresponds to IBC section 202. similar commodities, where the top of storage is greater than 6 feet Note: As used throughout chs.
7 SPS 361 to 366, not included as part of chs. SPS. 361 to 366 is intended to convey that the referenced requirements are not incorpo- in height. rated, and therefore cannot be enforced through chs. SPS 361 to 366. However, local (b) Neutral plane for a deep foundation means the level at ordinances may include the referenced requirements, as specified in s. SPS Note: IBC section addresses the scope of the IBC. For the scope of the Wis- which drag load, accumulated from the top down, added to the consin Commercial Building Code, see s. SPS Three or more attached town- long term static service load, equals the upward acting shaft resis- houses, as referenced in an exception under IBC section , are included within tance accumulated from the bottom up, added to the deep founda- the scope listed in s.
8 SPS Detached one and two family dwellings, as like- tion's toe resistance. wise referenced in an exception under IBC section , and elsewhere in the IBC, are not included within the scope listed in s. SPS , but are regulated in Wiscon- (c) Self service storage facility has the meaning given in sin by chs. SPS 320 to 325, in accordance with subch. II of ch. 101, Stats. (1) (g), Stats. History: CR 00 179: cr. Register December 2001 No. 552, eff. 7 1 02; CR. 01 139: renum. (1) and (2) to be Comm and Comm Register June (2) SUBSTITUTIONS. Substitute the following definitions for 2002 No. 558, eff. 7 1 02; CR 04 016: am. Register December 2004 No. 588, eff. the corresponding definition in IBC section 202: 1 1 05; CR 06 120: am.
9 Register February 2008 No. 626, eff. 3 1 08; CR 16 094: am., Register April 2018 No. 748 eff. 5 1 18. (a) Approved means acceptable to the department. Published under s. , Stats. Updated on the first day of each month. Entire code is always current. The Register date on each page is the date the Chapter was last published. Register April 2018 No. 748. Published under s. , Wis. Stats., by the Legislative Reference Bureau. SPS Wisconsin ADMINISTRATIVE CODE 16. (b) Automatic sprinkler system or automated fire sprinkler (4) (b) 7., Stats., Register February 2008 No. 626, eff. 3 1 08; CR 10 103: r. and recr. (1), (2) Register August 2011 No. 668, eff. 9 1 11; CR 16 094: renum. (1). system has the meaning given in s.
10 (2), Stats. to (1) (intro.), (a) and am., cr. (1) (b), (c), renum. (2) to (2) (intro.), (a) and am., Note: Section (2), Stats., reads as follows: Automatic fire sprinkler sys- cr. (2) (b) to (i), am. (3), Register April 2018 No. 748 eff. 5 1 18; correction in tem,' for fire protection purposes, means an integrated system of underground and (2) (h) made under s. , Stats. overhead piping designed in accordance with fire protection engineering standards. The system includes a suitable water supply, such as a gravity tank, fire pump, reser- voir or pressure tank or connection beginning at the supply side of an approved gate SPS Cheese factories classified as F 2. valve located at or near the property line where the pipe or piping system provides occupancy.