1 owner 'S MANUAL . DS2 Series 60 Cycle Self-Priming Centrifugal Pump MODELS. 1 HP 1-1/2 HP 2 HP 2-1/2 HP. DS2HE-191PL DS2HF-192PL DS2HG-102L DS2 HHG-53L. DS2HE3-191P DS2HF3-192P DS2HG3-102 DS2 HHG3-53. 293 WRIGHT STREET, DELAVAN, WI 53115 PH: 888-782-7483. 2012 Pentair, Inc. All Rights Reserved. S30 (10/31/12). READ AND FOLLOW General Safety SAFETY INSTRUCTIONS! WARNING. This is the safety alert symbol. When you see this symbol on your pump or in this MANUAL , look for Hazardous pressure! one of the following signal words and be alert to the Do not run pump against closed discharge.
2 Potential for personal injury: Release all pressure on warns about hazards that will cause seri- system before working on ous personal injury, death or major property damage if any component. ignored. Pump is designed as a lawn sprinkler only. To avoid warns about hazards that can cause seri- heat built-up, over pressure hazard and possible injury, ous personal injury, death or major property damage if do not use in a pressure tank (domestic water) system. ignored. Do not use as a booster pump; pressurized suction may cause pump body to explode.
3 Warns about hazards that will or can cause minor personal injury or property damage if Do not allow pump or piping system to freeze. Freezing ignored. can damage pump and pipe, may lead to injury from equipment failure and will void warranty. The label NOTICE indicates special instructions which are important but not related to hazards. Pump water only with this pump. Carefully read and follow all safety instructions in Periodically inspect pump and system components. this MANUAL and on pump. Wear safety glasses at all times when working on or Keep safety labels in good condition.
4 Around pumps. Replace missing or damaged safety labels. Keep work area clean, uncluttered and properly lighted;. store properly all unused tools and equipment. California Proposition 65 Warning Keep visitors at a safe distance from the work areas. This product and related accessories contain chemicals known to the State of California to cause cancer, birth defects or other reproductive harm. Before You Install Your Pump NOTICE: Well must not be more than 20' depth to Electrical Safety water. Wire motor for correct WARNING voltage.
5 See 1. Long runs and many fittings increase friction and reduce flow. Locate pump as close to well as Electrical section of possible: use as few elbows and fittings as possible. this MANUAL and motor name plate. 2. Be sure well is clear of sand. Sand will plug the pump and void the warranty. Ground motor before 3. Protect pump and all piping from freezing. Freezing connecting to power will split pipe, damage pump and void the warranty. supply. Check locally for frost protection requirements (usually pipe must be 12 below frost line and pump Meet National Elec must be insulated).
6 Trical Code, Canadian Hazardous voltage. Electrical Code, and local 4. Be sure all pipes and foot valve are clean and in Can shock, burn, or codes for all wiring. good shape. cause death. 5. No air pockets in suction pipe. Ground pump before Follow wiring instruc . connecting to power tions in this MANUAL 6. No leaks in suction pipe. Use PTFE pipe thread supply. when connecting motor to sealant tape to seal pipe joints. power lines. 7. Unions installed near pump and well will aid in Make workshops childproof; use padlocks and master servicing.
7 Leave room use wrenches. switches; remove starter keys. 8. Pump body may explode if used Do not touch an operating motor. as a booster pump. DO NOT use in a booster Modern motors are designed to operate at high appli cation. temperatures. To avoid burns when servicing pump, allow it to cool for 20 minutes after shut-down before handling. 2. Well Pipe Installation NOTICE: Use the installation method below which Priming plug matches your well type. CASED WELL INSTALLATION Priming tee 1. Inspect foot valve to be sure it works freely.
8 Inspect Suction strainer to be sure it is clean. pipe 2. Connect foot valve and strainer to the first length of suction pipe and lower pipe into well. Add sections of pipe as needed, using PTFE pipe thread sealant Standing water 20' (6 m) max. level (pump off). tape on male threads. Be sure that all suction pipe is leakproof or pump will lose prime and fail to pump. Install foot valve 10 to 20 feet below the lowest level Drawdown water to which water will drop while pump is operating level (pump on). (pumping water level).
9 Your well driller can furnish 10-20' (3-6 m). this in formation. 3. To prevent sand and sediment from entering the pumping system, the foot valve/strainer should be at At least 5 feet ( m). least 5 feet above the bottom of the well. Foot Valve 4. When the proper depth is reached, install a sanitary well seal over the pipe and in the well casing. Tighten the bolts to seal the casing. 828 0993. 5. When using a foot valve, a priming tee and plug as Figure 1 Cased/Dug Well Installation shown in Figure 1 are recommended.
10 DUG WELL INSTALLATION. Same as cased well installation. DRIVEN POINT INSTALLATION. 1. Connect the suction pipe to the drive point as illustrated in Figure 2. Keep horizontal pipe run as short as possible. Use PTFE pipe thread sealant tape on male pipe threads. Multiple well points may Check valve be necessary to provide sufficient water to pump. 2. Install a check valve in horizontal pipe. Flow arrow on check valve must point toward pump. Steel drive pipe HORIZONTAL PIPING FROM WELL TO PUMP. 1. Never install a suction pipe that is smaller than the suction port of the pump.