1 Technical Data Effective September 1, 2016. Scene Wallstation Catalog# Prepared by Overview Project Date The Scene wallstations are pre-engraved low-voltage switches Comments Type that operate on 24 VDC power supplied by the Room Controller or DLVP power module. Each Scene Wallstation is designed to fit in a standard decorator opening and has two RJ45 ports for local network connections to eliminate wiring errors. Color match screwless wallplates included Features Low-voltage control for ON/OFF and dimming loads Personalize the Scene buttons with ON/OFF and dimming needs per output Pre-terminated control cable ready with RJ45 ports eliminate wiring errors Custom engraving options may be replaced in the field RC-6 TSB-P4. Programmable buttons using Pre-engraved Personal Remote buttons simplify delivery Technical Data Scene Wallstation . September 2016 .. Specifications Description/Operation The Scene wallstations are pre-terminated control cable ready and Voltage 24 VDC supplied from Room Controller work immediately upon power up.
2 Scene wallstations are fully Electrical Class 2, LPS functional out-of-the-box but can be customized to meet needs using Connection Ports Two RJ45 ports a personal remote to adjust and save the Scene settings. Button Large buttons: 2 or 3. Configurations Installation Small buttons: 2, 4, 5, 6. Installation Standard decorator opening Low-voltage devices are connected using pre-terminated control cables (ordered separately). Operating Temperature: 32 F to 104 F (0 C to 40 C). Environment Relative humidity: Less than 95%, non-condensing Sample Scene Wallstations For indoor use only Size H x W (121mm x 83mm). Standards UL 508 Listed Scene 1 All On Scene 1. Scene 1. Scene 2 Scene 1 Scene 2. Scene 3 Scene 2 Scene 3. Scene 2. Scene 4 Scene 3 Raise Scene 5 Scene 4 Lower All Off All Off All Off All Off RC-3 TLB-P1-* RC-6 TSB-P2-* RC-6 TSB-P3-* RC-6 TSB-P4-*. Preset Wallstation Preset Wallstation Preset Wallstation Preset Wallstation Engraving Relay Style Zone/ Zone/ Zone/ Address Dimmer 1 Dimmer 2 Dimmer 3.
3 All relays ON N/A N/A N/A N/A. Scene 1: All relays ON =50% =50% =50% 12. Scene 2: All relays ON =100% =100% =100% 13. Scene 3: All relays ON =50% =100% =50% 14. Scene 4: All relays ON =30% =0% =25% 15. Scene 5: All relays ON =20% =20% =20% 4. Scene 6:** All relays ON =100% =100% =100% DIP #4. All relays OFF N/A N/A N/A N/A. *Button defaults when shipped **Not available in a Wallstation configuration 2 Scene Wallstation Technical Data . September 2016.. Room Controller Personal Remote DLVP Personal Remote Zone Raise/. Lower Dimmer 1, 2, 3 Raise/Lower Zone Control Relay 1, 2, 3 ON/OFF. AUX. Open/Close Solatube/Shade Output R1 R2 R3. Programmable Open/Close Scene Buttons SET AUX Shade or Solatube SET. Saves Current light levels and relay S1 S2 S3. states to selected Scene SET. S4 S5 S6 Scenes 1-6 Preset S1 = Button Address 12 Saves current light S2 = Button Address 13 levels to selected To save Scene press SET and select Scene S3 = Button Address 14 Scene S4 = Button Address 15.
4 S5 = Button Address 4. S6 = Auto On Scene (DIP #4 UP). Room Controller Personal Remote HHPR-RC. Sample Room Controller System Topology Ceiling Room Controller RC3DE. Adjustable daylight Up to 6 Lighting Zones sensor dome (3 Relays and 3 Dimmers). Daylight sensor Wall DS-FMOIR. OCC-RJ45. Dual Technology Wall/Corner Occupancy/Vacancy Sensor Egress Output (or additional lighting zone). OCC-RJ45. OAWC-DT-120W. BMS Output (BMS integration). Row 1. OCC-RJ45. Entry Row 2. Row 3. All Off Raise Lower All Off 20A Receptacle Control SPRC-R-20-120 Teacher Station Entry Station RC-6 TSB-TS7-* RC-2 TLB-EC1-*. Output for Egress Lighting Control, BMS output or Receptable Control Sample DLVP System Topology Daylight Sensor Power Module Low-Voltage Lighting Cables TRIM. LOW HIGH. STATUS. TEST. RESET. DEMAND CLOCK ALERT. +- +- +- relpuoC rosneS ycnapuccO. eulB. 54JR-CCO :ledoM. deR. kcalB. nworB. 4 5 6. Zone / Area Partial Off Partial On Occ / Vac 1 1 REC.
5 Occupancy BMS/OUT. Dual Technology 1 2 3 4 5. Coupler V Y Y A. O N N Z. Low-Voltage CeilingOccupancy Light Fixtures Sensor 1 2 3 4 5. 10% - - 2 2 SWITCH. 1 2 3. 20% + - PACK. 30% - +. 40% + +. SENSORS WALL LOW VOLTAGE OUTPUTS. DEMAND. RESPONSE. LL053001EN. General Entry Lighting Whiteboard Quiet Time All Off A/V Mode Raise Pre-terminated Occupancy Sensor Coupler Blue Model: OCC-RJ45. Lower Red Black Control Cables Brown Entry Teacher Wallstation Wallstation BMS/Egress Output Receptacle Rated Switchpack 3. Technical Data Scene Wallstation . September 2016 .. Ordering RC - 6 TSB - P1 - W. RC Insert Color Scene Wallstation W = White B = Black Number of Buttons V = Ivory G = Gray 2,3 = Large Buttons TLB. 4,5,6 = Small Buttons TSB. Button Engraving P1 = Scene 1, Scene 2, All Off (3 TLB). P2 = Scene 1, Scene 2, Scene 3, Scene 4, Scene 5, All Off (6 TSB). P3 = All On, Scene 1, Scene 2, Scene 3, Scene 4, All Off P4 = Scene 1, Scene 2, Scene 3, Raise, Lower, All Off (6 TSB).
6 Additional Options Catalog # Description HHPR-RC Room Controller Personal Remote LVHH-02 DLVP Personal Remote Eaton 1121 Highway 74 South Peachtree City, GA 30269. For service or Technical assistance: 1-800-553-3879. 2016 Eaton All Rights Reserved Printed in USA. Publication No. TD503086EN Specifications and dimensions subject to September 28 2016 change without notice.