1 Data and Installation Interface Modules for Vigilon by Honeywell low voltage (LV) Input/Output S4-34410* S4-34420* S4-34450* S4-34490*. S4 1- input Interface S4 1- output & S4 4- input / output Plastic box Module 1- input Interface Interface Module ( low voltage ) Module ( low voltage ) ( low voltage ). Channel 4. Channel 3. Channel 2. Channel 1. output input input COM. NO. NC. 0V. 0V. 0V. 0V. L2. L1. L2. L1. 0V. 0V. L2. L1. 1- Allen key 2 - M4 Screws 2 - M4 Posi Pan Screws 7 - Hole plugs 1- End-of-line 2- 10K Resistors S4-34492*. 1- End-of-line Capacitor unit Metal box Capacitor unit 2- 10K Resistors 8- 10K Resistors S4-34491. DIN rail mount * - LPCB approved bracket These instructions cover the above LPCB approved interface modules Installation and accessories.
2 These interface The S4 interface modules can be mounted in modules are designed for use with other equipment housings using the DIN rail Vigilon and 34000 fire alarm control mount brackets (S4-34491). A module can also 042ba panel. Each module includes a loop be fitted into a plastic box (S4-34490) or metal isolator for device isolation. Each interface module box (S4-34492). The boxes have cable use one of 207 available device addresses on a loop termination points on the enclosure for incoming and responds to regular polls from the control panel cables. reporting the type of device and the status Connect to loop Module (open/normal/short) of its supervised input circuit(s).
3 Cable screen DIN rail Features Slide &. lock Analogue addressable communications Hook and push to lock Built-in type identification automatically identifies DIN rail mount bracket these devices to the control panel 7 - top cable Reliable communication technique with high noise entry points immunity 64. Soft or SAFE addressing Allen Common mounting options including surface key 106. mount, panel mount and DIN rail mount Dual-colour LEDs Plug-in terminal connections for ease of wiring Box EN54-17:2005 and EN54-18:2005 Door Module 3 - box fixing points (Includes 1-keyhole). M4 Screws 140. Cables Metal backbox The cables recommended for wiring the input / output 80.
4 Lines are the same as those used for loop wiring, see Lid instructions supplied with the fire control panel. Module M4 Screws 7 usable cable entry points 4188-873_issue LV Interfaces 1. Data and Installation Interfaces ( low voltage ). Maximum cable usage per circuit to minimise false alarms by suppressing a fire input for a period of time defined during commissioning. &. The zone reset period can be extended to allow for different types of fire detectors. Cable usage per circuit of: Zone circuit - 100 metres maximum Clean contact input circuit - 300 metres maximum Channel 4. Channel 3. Channel 2. Channel 1. LED output - 30 metres maximum Relay output - unlimited.
5 Light pipe Removable End-of-line (EOL) devices terminal blocks An input circuit require in series with the contacts a 10K resistor plus a 10K EOL resistor (supplied). A zone input circuit is monitored with an EOL Link Configurations capacitor unit (supplied). Zone input functionality A zone input can have conventional detectors and Relay output Other manual call points (MCPs) connected. All MCPs must mode modes (factory settings). have a 470 Ohms or 3V9 zener diode in series with Confirmation normally open contacts. The zone input can take a input maximum load of up to 2mA at 24V nominal (with Zone input minimum operating voltage of 18V).
6 The zone circuit Switch input must be terminated with an EOL capacitor unit. LED output modes Confirmation input / output functionality Configure the links to the required mode. An input and an output of a module can be paired to operate in a confirmation mode. External equipment S4 1- output & 1- input Interface can send an acknowledgement upon receiving a signal from the module, this is called 'confirmation This interface module can be used to control a input '. External equipment can also receive an resistive load of up to 1A @ 30 Vdc/ac via a set of acknowledgement from the module upon sending it a single pole change over contacts, see wiring signal, this is called 'confirmation output '.
7 Diagrams. In addition there is an input to allow the monitoring of the external equipment. In this application the input must be configured as a S4 1- input Interface confirmation input . A confirmation input generates a The single input interface module monitors a circuit of fault if a change of state is not seen within the either normally open or closed contacts. The input predefined period of a specific output . can be programmed as a fire, fault, supervisory or confirmation input . Optionally it is also possible to Configuration configure the input for a zone of conventional ". detectors and MCPs. In all input modes the interface will detect short and open circuit faults.
8 Use the Commissioning Tool Version or greater to commission these S4 4- input / output Interface interface modules. The quad Input/Output interface module can be configured to provide any combination of up to four inputs or outputs. An output of either normally open or normally closed relay contacts can be used to control a load of up to 1A @ 30 Vdc/ac. Optionally an output can be configured to provide at 24V dc to drive an LED that can be normally On or normally Off. An input can be programmed as a fire, fault, supervisory or confirmation input . Additionally it is possible for channel 1 to be used as a Zone input , which allow connection of conventional detectors and MCPs to this module.
9 Zone input can be configured to have alarm validation feature and configurable reset time. The alarm validation feature can be used 2 4188-873_issue LV Interfaces Interfaces ( low voltage ) Data and Installation Wiring diagrams & The loop cable screen must be continued through each interface module. The loop, switch input , zone input and LED output cable screens where used must connect to an earth terminal. S4 1- input module S4 4- Input/Output module connection details connection details Z- Zone input Relay Outputs NC / NO. Mode see Note 4. LED output See Note 1. see Note 3. Zone input see Note 2. Z+ EOL. EOL Switch *. Capacitor unit * input COM.
10 10K. 10K. Switch input Loop L2+. Loop 0V. Loop L1+. Loop 0V. EOL10K. 10K Mode EOL. *. *. *. *. *. Z+ Z- 12 11 10 9 88 77 66 55 44 33 22 11. Channel 4. Channel 3. Channel 2. Channel 1. Loop L2+. Loop 0V. Loop L1+. Loop 0V. #. S4 1- output & 1- input module 12 11 10 9 8 7 6 5 4 3 2 1. connection details Confirmation output - Relay input contact rating *. (Optional) 1A 30V ac/dc Resistive load COM. Note 1 - When the input is configured as a Zone input 10K. EOL 10K. NO. NC. it is possible to attach conventional detectors and MCPs (with 470 Ohms or 3V9 zener Loop L2+. Loop 0V. Loop L1+. Loop 0V. diode in series with normally open contacts), maximum load is 2mA @ 24V nominal (18V minimum) with End-of-line capacitor.