1 vive PowPak Fixture Controls Wireless Fixture Controls 369918g 1 vive PowPak Fixture Controls The PowPak wireless xture control is a radio-frequency (RF). device that Controls either the Lutron EcoSystem or 0 10 V- electronic uorescent ballasts and LED drivers (depending on model). This is based on RF input from Pico remote Controls , Radio Powr Savr wireless sensors, or wired inputs from the PowPak xture sensor. The control module mounts to a xture or a junction box. Communication with RF input devices is accomplished using Lutron Clear Connect RF Technology. See Applications and Selecting the Right control for more details on selecting the appropriate Controls for your application. The PowPak xture sensor (optional) mounts to the ceiling or to a xture and measures light in the space (daylighting) while detecting people moving within an area to determine passive infrared occupancy.
2 The sensor Controls the lights to balance light level in the space, combining convenience, exceptional energy savings, PowPak Wireless Fixture control and ease of installation. The sensor contains two wires which connect to the PowPak wireless xture control . These products are also compatible with the vive hub which enables a simple setup process using a standard web browser on any Wi-Fi enabled phone, tablet or computer. It also enables control and monitoring of all vive devices. The vive hub can be added at any time. System reprogramming will be required. For a complete list of features supported with the vive hub, see speci cation submittal 369902 at Note for Replacement: FCJS - the S model can replace the PowPak xture sensor non- S model. Models Available Model Number Description FC-SENSOR PowPak xture sensor (occupancy).
3 FC-VSENSOR PowPak xture sensor (vacancy) 1. FCJS-010 2 PowPak wireless xture control for 0-10 V- ballasts and drivers 3. FCJS-ECO PowPak wireless xture control for EcoSystem ballasts and drivers FCJS-010-EM Emergency PowPak wireless xture control for 0-10 V- ballasts and drivers FCJS-ECO-EM Emergency PowPak wireless xture control for EcoSystem ballasts and drivers 1. Lights do not turn on automatically with a vacancy sensor. A Pico remote control is needed to turn on the lights. 2. For a bulk pack of 8 pieces, order FCJS-010-BULK8. 3. For a bulk pack of 8 pieces, order FCJS-ECO-BULK8. S P E C I F I C AT I O N S U B M I T TA L Page 1. Job Name: Model Numbers: Job Number: vive PowPak Fixture Controls Wireless Fixture Controls 369918g 2 Applications and Selecting the Right control Suggested applications: Daylighting: PowPak Fixture Sensor: Radio Powr Savr vs.
4 PowPak Fixture Sensor Great for individual control in cubicles PowPak wireless xture Controls have two options for daylighting. The PowPak xture sensor can be used for Maximize energy savings ( xtures in unoccupied simple, out-of-the-box daylighting. The Radio Powr Savr spaces do not turn on). wireless daylight sensor can be added for the ability to Simpli es the determination of what's needed for a job adjust and ne tune daylighting settings. Radio Powr Savr daylight sensors provide the ultimate Radio Powr Savr Sensors: exibility in daylighting: target light level (tuning) and Cover large areas with a single sensor gain value (through calibration) can be adjusted Sensor can mount anywhere in the space independently. Daylighting rows/zones can be setup so that multiple xtures dim in unison (also known as fixtures assigned to Radio Powr Savr occupancy grouping ).
5 Radio Powr Savr daylight sensors can be sensors turn on and off together placed anywhere since they are completely wireless, and In order to have a row of xtures dim up or down performance can be optimized through placement and together in response to daylight, a Radio Powr Savr ne tuning. daylight sensor must be used PowPak xture sensors are an easy way to add simple daylighting to a localized area without requiring setup. PowPak xture sensors are quick to install with a two- wire connection, and calibrate automatically. Each PowPak xture sensor should be mounted within 2 ft ( m) of the xture it is controlling. S P E C I F I C AT I O N S U B M I T TA L Page 2. Job Name: Model Numbers: Job Number: vive PowPak Fixture Controls Wireless Fixture Controls 369918g 3 The following can be used per each PowPak wireless xture control : Wired: Maximum of 1 PowPak xture sensor.
6 Note: Only 1 PowPak wireless xture sensor can be wired per PowPak xture control . Grouping more than 1 PowPak wireless Pico remote control xture sensor to control a group of PowPak (up to 10). wireless xture Controls requires adding a vive hub. Wireless: PowPak wireless Maximum of 10 Pico remote Controls xture control Radio Powr Savr occupancy sensor Maximum of 10 Radio Powr Savr (up to 10). occupancy sensors PowPak xture Maximum of 1 Radio Powr Savr Link Test sensor Link Test daylight sensor Radio Powr Savr daylight sensor (1 maximum). Notes: When using a Radio Powr Savr daylight sensor in conjunction with both a PowPak wireless xture control and PowPak xture sensor, the Radio Powr Savr daylight sensor will provide the daylighting input to the control module, and the PowPak xture sensor daylighting input will be ignored.
7 When using a Radio Powr Savr occupancy sensor in conjunction with both a PowPak wireless xture control and PowPak xture sensor, occupancy data from both sensors is used; either one detecting occupancy will turn the lights on, and the lights turn off only when both sensors have gone vacant (no longer detect occupancy). Grouping can be accomplished by following the basic procedure described in the install guide found at for putting multiple control modules into association mode. This enables a Radio Powr Savr occupancy sensor or Radio Powr Savr daylight sensor to group and control more than one xture together. Radio Powr Savr occupancy sensors can be used with the PowPak xture sensor to add coverage area. S P E C I F I C AT I O N S U B M I T TA L Page 3. Job Name: Model Numbers: Job Number: vive PowPak Fixture Controls Wireless Fixture Controls 369918g 4 Speci cations PowPak Fixture Sensor Regulatory Approvals Settings FC-SENSOR, FC-VSENSOR: Occupancy sensor timeout ( xture sensor): 15 minutes cULus Listed Utilizes a green laser pointer (by others, not a Lutron Complies with requirements for use in other spaces product) to associate Pico remote Controls and Radio used for environmental air (plenums) per Powr Savr sensors to PowPak wireless xture Controls NECR 2014 (C)(3) via RF.
8 See Lutron Application Note #407. Power/Load (P/N 048407 at ) for more information. Operating voltage: 12 V- Green laser speci cations: Operating current: 25 mA Wave output: constant IEC SELV / NECR Class 2 Wavelength: 532 nm Output power: 5 mW maximum Environmental 2-wire connection between a PowPak xture sensor Ambient operating temperature: 32 F to 104 F. and a PowPak wireless xture control (0 C to 40 C), 0% 90% humidity, non-condensing;. The wires are interchangeable to eliminate miswiring indoor use only The sensor comes with 2 ft ( m) of wires Warranty If hanging pendant xtures, the maximum wire 5 Year Limited Warranty. For additional Warranty length between xture sensor and xture control is information, please visit: 12 ft ( m). Sensor should be mounted no more than 2 ft ( m) from the xture.
9 Wiring Sensor wires are IEC SELV / NECR Class 2 rated Sensor ! WARNING DANGER. Eye injury and/or blindness hazard; avoid direct eye exposure to laser beam. Green Laser Use of laser pointer is NOT recommended for use with Lutron products located near re ective surfaces. Do NOT aim or shine laser pointers at any person, pet, vehicle, or aircraft directly, or through re ection by mirrors or other shiny surfaces. Do NOT view the laser beam through binoculars, magnifying glass, or other optical devices. Do NOT allow children to use laser pointers. Read and follow the laser pointer manufacturer's instructions on safe use. In the event of injury, get medical attention immediately. S P E C I F I C AT I O N S U B M I T TA L Page 4. Job Name: Model Numbers: Job Number: vive PowPak Fixture Controls Wireless Fixture Controls 369918g 5 Speci cations (continued).
10 PowPak Fixture Sensor (continued) PowPak Wireless Fixture control Features Regulatory Approvals Occupancy Sensor: Title 20/24 certi ed lighting control device. Complies Passive infrared motion detection with exclusive Lutron with Title 20 and Title 24 section XCT Technology for major and minor motion detection. Enables compliance with lighting control requirements 360 eld-of-view. in ASHRAE and IECC. Up to 300 ft2 ( m2) major motion coverage and 150 ft2 Complies with requirements for use in other spaces ( m2) minor motion coverage. used for environmental air (plenums) per NECR 2014 (C)(3). Daylight Sensor: Listed in accordance to CAN/ULC with Daylight sensor has simple, automatic calibration a Flame Spread Rating of 0 and a Smoke Developed out-of-the-box. Classification of 40, with a minimum spacing of 6 ft Designed to give a linear response to changes in ( m) off center perceived light level.